Voltage nonsinusoidality ratio must not exceed 8%.
Ripple DC voltage must not exceed 1%.
The distance from high-voltage inputs of RD-250 to power oject not less than 0.5 m.
Measuring range DC voltage (average): from 25 to 250 kV.
Measuring range of the AC voltage (RMS): from 15 to 170 kV.
Bandwidth on AC metering: 47,5-52,5 Hz.
Input impedance of high-voltage unit RD-250 on DC 1600 ± 2 MOhm.
Input impedance of high-voltage unit RD-250 on AC, 50 Hz: 200 ± 5 MOhm.
Maximum permissible relative error of DC and AC measurement: ± 1,0%.
Power supply of HV unit and remote control unit: 4xNi-MH batteries AA of 1.2 V and a capacity of 1.8-2.1 A • h:
Supply voltage: 5 ± 0,2V.
Radiochannel range: at least 5m.
Continuous operation of RD-250 with an input voltage up to 150 kV: up to 8 hours.
Operation mode setup time after the power:1 minute.
Dimensions: d530x1825 mm;
Weight - 36,1 kg